|Place of Origin:||Guangdong, China (Mainland)|
Payment & Shipping Terms:
|Minimum Order Quantity:||1 Unit/Units|
|Packaging Details:||Carton or Wooden case|
|Delivery Time:||7-10days after payment arrived|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Supply Ability:||1000 sets per year|
|Pipeline Material:||UPVC ,Stailess Steel||Membrane:||Hollow Fibre Membrane|
|Output Water PH:||6.4-7.2||Voltage:||220/380V,50/60HZ|
8000T Industrial Ultrafiltration Water Processor,
Membrane Industrial Ultrafiltration Water Processor
The attention should be paid to the use of Hollow Fibar UF Membrane .
8000T Industrial Ultrafiltration Large Water Processor,Hollow Fiber Membrane
|1||Regularly ,The UF Membrane can intercept bacteria ,But it can’t kill bacteria ,The UF Membrane that is good interception rate also can’t ensure that bacteria don’t grow in the clean area ,where the bacteria can propagated largely .Directly affects permeated the water quality ,for example ,some mineral water products appear translucent filamentous white floc mold,mainly caused by mold contamination .Therefore,regular sterilization of the working environment and filtration system must be carried out regularly.the operation cycle of sterilization is determined according to the condition of the raw water ,For the ordinary top water in the city ,7--10day in the summer ,and 30--40 days in winter,20--30 days in spring and autumn season .As the underground water is the feed water ,the sterilization period is shorter .The sterilized drugs can be circulated or soaked for about half an hour by using 500--1000mg/l Naclo3 solution or 1% hydrogen peroxide water solution .|
|2||Due to each ultra filtration element must be added protective fluid before leaving factory,Rinse the protective fluid thoroughly before use ,First rinse with the low pressure (0.1 MPa) water for 1 hours ,and then rinse with the high pressure water (0.2MPa) for 1 hours,No matter the high or low pressure washing ,the water discharge valve of producing water should be opened fully.when using producing water ,should check &confirm that there are no any bactericide.|
|3||The UF element should be light to take and lay ,then pay attention to protection .Due to the UF Membranes are precision components ,so we should be careful when using and install ,and it should be light to take ,but not to throw away .if the elements are discontinued ,They should be rinsed clean with water and sterilized with 0.5% formaldehyde solution ,and seal it well . The system must be antifreeze treatment in winter ,if not ,the system may be broken .|
The Comparision of the kind of membrane :
|Hollow Fibre||Spiral-wound||Ceramic Tubular||Plate and Frame|
|Total Dissolved Solids(mg/L)||<1000||<600||<500|
|Total Suspended Solids(mg/L)||<500||<450||<300|
|Oils and Greases(mg/L)||<0.1||<0.1||<0.1|
|Solvents , phenols(mg/L)||<0.1||<0.1||<0.1|
How to service
100% factory tested before shipment
One Year's Quality Warranty
--General technical advice and business consultation.
--Suitable scheme and equipment as order.
--Designing as special requirement.
--Complete plan with technology and production line equipment.
2. After-sales Service
-- One year warranty.
--Inspecting equipments in every working procedure.
--Assisting foundation construction.
--Dispatching engineer to install and debug.
--Training the first-line worker on site;
--Visiting clients and solving production problem.
--Life-long maintenance service.