|Place of Origin:||Guangdong, China (Mainland)|
Payment & Shipping Terms:
|Minimum Order Quantity:||1 Unit/Units|
|Packaging Details:||Carton or Wooden case|
|Delivery Time:||7-10days after payment arrived|
|Payment Terms:||D/A, L/C, D/P, T/T, Western Union, MoneyGram|
|Supply Ability:||1000 sets per year|
|Material:||FRP Or Carbon Steel With Rubber Lining||Diameter:||200mm To 3000mm|
|Filling Material:||Cation Resin,anion Resin Or Mixed Bed||Control:||Autotrol Fully Automatic Multiple Valve Control Or Manual|
|Work Procedure:||Exchange Softening, Backflushing, Salt Feeding, Regenerating,etc.||Product Water:||Consistent Quality With Low Residual Hardness|
|Application:||For Boiler, Air-conditioner, Chemical, Light Textile,etc.|
ion exchange water treatment plant,
ion exchange ro water purifier
1. Feed water of steam boiler, hot water boiler exchanger,evaporative condenser,air conditioner ect.
2. Domestic water of hotel, restaurant, office building, apartment ect;
3. Water softening for food and beverage, brewing, washing, printing, chemical and medicine ect.
Working process includes:
|Step 1||Exchange Softening|
|Step 3||Salt Feeding|
|Step 4||Resin Regenerating|
|Step 5||Fast Rinse|
Multimedia filter and activate carbo filter are pre-treatment filters which is done by filter media (quartz sand, activate carbon, gravel, anthracite..etc) to purify raw water first then enter into water softener.
As Calcium and Magnesium are the main substances for the hardness water. In order to exchange Ca2+, Mg2+(main component of scale), cation exchanger (softener) is needed. After running for a long time, resin shall be regenerated by sodium chloride(NaCl).
Reaction equation of softening (R is resin):
Reaction equation of regeneration:
1.In order to cut down the cost, can change into manual control system.
2.If the device run for 24 hours continuously, can choose two sets alternately, one for spare one
3.According to the outlet water's quality, can add some device before water softener.
Like Multimedia Filter(effectively remove sand, iron rust, colloid and seston) and Active Carbon Filter
(effectively remove remained chlorine and pesticides as well as pigment, odor, organice).
4.Outlet water's quality can reach state standard of low pressure boiler water.
|water inlet pressure||0.18-0.6Mpa|
|raw water's hardness||<8mmol/L|
|outlet water's hardness||≤0.03mmol/L|
|ways of regeneration||downstream/upstream|
|ways of control||time/capacity|
|ways of operation||automatic/manual|
|exchanger||001*7highlyacid resin for ion exchange|